SaniSweep Compact, the Chlorine Dioxide
The Sanipur solutions for Legionella remediation with ClO2.
Chlorine dioxide was shown to be an effective biocide in fighting Legionella into hot water networks.
Together with a suitable Legionellosis Prevention plan SaniSWEEP compact helps to solve Legionella problems in hospitals, clinics, hotels and resorts.
The SaniSWEEP chlorine dioxide is not pH dependent and produces less disinfectant by-products compared with traditional chlorine.
The chlorine dioxide produced rate of SaniSWEEP generators varies from 0.01 to 5 lb/h which makes them suitable for any type of process application.
How does it work?
Chlorine dioxide is produced in situ by diluted solutions of NaClO2 and HCl.
Special GSM/GPRS WAP electronic controller allows a continuous control of Clo2 concentration, which does not vary with hot water consumption fluctuation (remotely stabilized cLo2 concentration without the need of an on-line analyzer). Also at zero consumption it able to keep the chlorine dioxide.
Look at the graph on the side. Are examples of registration and you can see how the chlorine dioxide dosage is always recorded in 24h.
|Production max||DXT 15 DIC from 1 to 15 g/h
DXT 30 DCP from 5 to 35 g/h
|Working Pressure max||10 bar|
|Reagent dosing amount max||0.38 l/h|
|Power Supply||Standard: 220 Vac 50/60 Hz
Optional: 110 Vac 50/60 Hz
|Power installed||1.5 kW|
|Class of production||IP 65|
|Reagents to be used||Hydrolic acid