SaniSweep Standard, the Chlorine Dioxide
The Sanipur solutions for Legionella remediation with ClO2.
SaniSweep standard Technologies
Chlorine dioxide was shown to be an effective biocide in fighting Legionella into hot water networks.
Together with a suitable Legionellosis Prevention plan SaniSweep standard helps to solve Legionella problems in hospitals, clinics, hotels and resorts.
The SaniSWEEP chlorine dioxide is not pH dependent and produces less disinfectant by-products compared with traditional chlorine.
The chlorine dioxide produced rate of SaniSWEEP generators varies from 0.01 to 5 lb/h which makes them suitable for any type of process application.
How does it work?
SaniSweep standard units work with diluted chemicals hydrochloric acid and sodium chlorite.
Reagents dosing system with two electro-magnetic pumps with electronic control on board completely equipped with knob, valve and drain of sending line.
The production reactor is controlled by sensors for dosage and it is contained in a dust proof polyester box made with a ventilation system.
Take a look at the graph on this side…
Special GSM/GPRS WAP electronic controllers allows a continuous control of ClO2 concentration, which does not vary with hot water consumption fluctuation.
|Production max||from 5 to 1500 g/h|
|Working Pressure max||10 bar|
|Reagent dosing amount max||from 0.9 to 39 l/h|
|Power Supply||Standard: 220 Vac 50/60 Hz
Optional: 110 Vac 50/60 Hz
|Power installed||1.5 kW|
|Class of production||IP 65|
|Reagents to be used||Hydrolic acid